Oil and gas boilers belong to the category of special equipment in China. There are strict operating specifications and standards for boiler manufacturers' manufacturing, transportation, installation and users' later use and maintenance.Zhengzhou Fangkuai Boiler Factory summarizes some problems that need to be paid attention to when building the boiler room of oil and gas boilers, to help you better use this kind of boiler equipment.
1. Boiler room shall not be connected with Class A, Class B and Class C fire risk room using flammable liquid.If connected with other production plants, the application of firewall separation.Waste heat boilers are not subject to this restriction.
Boiler room belongs to class D production workshop, oil tank room, oil pump room belongs to class C production and delivery room, gas regulating room belongs to class A production and delivery room.
2. The exterior wall or roof of the boiler room should be at least equivalent to the pressure relief area of 10% of the area of the boiler room (such as glass Windows, skylights, shutters, etc.), and the pressure relief mouth should avoid densely populated places.
3, boiler room should be equipped with emergency lighting and evacuation indication signs, emergency lighting voltage shall not be higher than 36V.